Furnace maintenance & inspection
Condenser fan motor replacement.
Making use of the combustion analyzer, checking for carbon monoxide.
Propane tanks for the generator, with this system you will have power when the lights go out.
Maintenance is key.
Hepa filter mounted in return air duct. Does your family require better air quality? This is the proven method of filtering air, not a $30 from...
New Navien Tankless water heater
Replacing a failed Ventor Motor
BBQ line installation BBQ line installation, Duggans Mechanical, Excellence with Integrity. We have 16 years experience working on the hottest and...
Brand new A/C unit, no cooling. Compressor locked out due to a failed contact in the thermostat. Replaced thermostat. Running well.
Found a cracked heat exchanger during an inspection—this is very dangerous. Customer chose to go with a new Payne (carrier) furnace.