Furnace maintenance & inspection
Condenser fan motor replacement.
Not good—make sure your carbon monoxide detector is working.
Fireplace maintenance & cleaning
Brand new A/C unit, no cooling. Compressor locked out due to a failed contact in the thermostat. Replaced thermostat. Running well.
Hepa filter mounted in return air duct. Does your family require better air quality? This is the proven method of filtering air, not a $30 from...
Replacing a failed Ventor Motor
Not a good idea—don’t cover your vents for any reason. These socks were having a great affect on equipment operation.
Found a cracked heat exchanger during an inspection—this is very dangerous. Customer chose to go with a new Payne (carrier) furnace.
Making use of the combustion analyzer, checking for carbon monoxide.